With rising costs of energy, slimmer profit margins and tighter specifications on product quality, the metals-processing industry continues to look for ways to increase productivity and reduce costs. The “Roadmap for Process Heating Technology”, published in 2001, identified the following critical requirements for the industry:
- Advanced sensors
- Predictive models
- Increase productivity
- Decrease total costs
- Decrease product costs
- Improve energy efficiency
- Few direct process-measurement sensors
- Few low cost, accurate, rugged, non-intrusive sensors
- Excessive failures and inaccuracies of thermocouples
- Inability to reliably control processes
- Lack of smart controls
- Lack of cost-effective control devices
Five-Step Process to Optimize a Manufacturing FacilityTo improve productivity and reduce costs using automation and advanced control requires a strategic view of the issues facing the manufacturing facility. Only by first understanding the big picture can a proper advanced controls strategy be designed. While the literature and market are flooded with products and claims that promise to solve “all of your problems” using state-of-the-art control technology, there is no single, right control solution for all manufacturing facilities. The answer depends on correctly framing the problems and understanding all of the issues that are being faced by a facility.
To facilitate this framework, Figure 1 presents a five-step process for optimizing a facility using automation and advanced controls. Like any other major business decision, developing an advanced control and optimization strategy should be carefully considered, first by understanding available technology and overall facility objectives followed by a thorough assessment of the entire manufacturing operation. This information is critical to determining how to best utilize the company’s resources. Only after all of this information has been collected can actual project work begin. Finally, after project completion, results must be tracked and lessons documented for future use.
By following the five steps to developing an advanced control and optimization strategy (Fig. 1) presented in further detail in this article, the chances of reaching true optimal operation are greatly increased.
Advanced control technology is not new. The opportunities that exist for advanced control technologies are in its application to new processes and industries. For example, Model Predictive Control (MPC) – a multivariable control strategy – has been in use for over 20 years in the refining industry with more than 2,000 applications by the year 2000. In the 1990s, this technology was further extended to other industries, including petrochemical, chemical, pulp and paper, and food processing. MPC is currently used by Air Products and Chemicals, Inc. to help control and optimize large complex plants.
Can this technology be used in the heat-treating industry? Because most of the processes used in heat treating are highly complex, the answer is a resounding yes. Currently, there’s a gap between state-of-the-art control technology and applications in the heat-treating industry. Three factors explain this gap and why the issues facing the industry today are similar to those faced 20 years ago. They are: availability of low-cost, reliable sensors, which are critical because to control a variable, it must first be reliably and consistently measured in real time; availability of cost-effective process-control solutions; and ability to extend existing control technology to new applications.
In the last five years, there’s been major progress in the use of sensor and regulatory control technology in the metal-processing industry, helping to close the gap created by the first two factors. The third factor, extending existing advanced control technology to new applications, can be accomplished with increased awareness and education.
Many of Air Products’ operating facilities are large, complex plants featuring nonlinear chemical processes that are run at conservative operating limits since they can be difficult to control. Traditional control strategies do a poor job of managing nonlinearities, interactions or multiple process constraints and typically react to process disturbances after they have already occurred. In addition, traditional controllers do not provide process optimization. Therefore, Air Products uses advanced control techniques like MPC to optimize and reliably control its plants – resulting in substantial, sustainable benefits.
A predictive controller, like MPC, generates new set points for variables based on the anticipated behavior of the process. These controllers have built-in dynamic models of the process and use them to predict what will happen based on past events. In addition, predictive controllers try to react and reject disturbances before the process is affected. MPC takes this a step further, taking into account economic variables, such as the cost of increasing a feed-rate, to determine the optimal operating conditions for the process.
For example, a predictive controller can be applied to a brazing process. Brazing is a heat-treating process that joins metals through the use of a filler metal and heat at a temperature below the melting point of the metals being joined. A successfully brazed joint is often stronger than the base metals being joined. In furnace brazing, the process can be run in a controlled gaseous atmosphere or in an evacuated chamber. Following brazing, the metals are cooled – often in a different zone of the furnace.
A continuous belt furnace is pictured in Figure 2. Typical quality variables for a brazing process include parameters such as joint strength, distortion or an aesthetic parameter, all of which are extremely difficult or costly to measure online. Process parameters including furnace temperatures, furnace pressures, atmosphere compositions and furnace dew point are easier to measure and should be used in the control strategy.
For brazing operations, the potential benefits of advanced control and furnace optimization include improved part quality and performance, reduced furnace cycle times, improved oxidation/reduction potential control, reduced atmosphere consumption and early detection of furnace maintenance issues.
Step 2: Overall Facility Objectives
Control-system design is dependent on the overall objectives of the operating facility. Is increased capacity the most important goal? If so, an advanced control strategy may increase operating costs in order to maximize production. Alternatively, perhaps maintaining fixed production at the lowest possible cost is the most important objective. In this case, an advanced control strategy is essential because the controller will need to simultaneously focus on reducing process variability and determining the most economically optimal operating conditions. Traditional control strategies cannot do both. However, if the objective is to maintain consistent process quality on a relatively simple process by reducing variability, a model-based controller may not be necessary.
As noted previously, it is critical to define all of the objectives from an overall facility perspective prior to beginning any project work. This will enable prioritization of projects and provide the best utilization of the facility’s available resources.
Step 3: Assessment
Once the facility’s objectives and the available control and sensor technology to meet these objectives have been identified, the next step is to conduct a comprehensive productivity assessment of the entire manufacturing operation. A cross-functional team utilizing a defined, rigorous work process should do this. These experts can identify specific improvement possibilities, including potential projects that can result in savings derived from labor reduction, energy reduction, yield/usage improvement, volume increases and quality improvements.
The assessment should concentrate on, but not be limited to, automation and advanced control. The result of the assessment is a detailed list of productivity improvement projects, each with a defined scope and containing estimated costs, benefits and payback. It is critical to assess the entire facility and prioritize the list of possible projects. In many cases, optimizing a single unit operation may cause problems in another part of the facility, resulting in suboptimal operation of the entire plant. In other cases, reducing variability in an upstream process will improve performance in downstream units. The largest gain in productivity may not come from installing the advanced control system but rather from automating difficult operator tasks or in measuring previously unmeasured variables. Projects should be prioritized and implemented in an order that makes the most sense, taking into account the financial and operational objectives of the facility. Such an assessment can result in a concrete implementation plan for overall optimization of the plant in the most efficient way.
Step 4: Implementation
It usually isn’t practical or feasible to implement every project identified by an assessment. The projects should be prioritized and implemented in such a way as to begin accruing benefits and, at the same time, laying the foundation for future projects. For example, before implementing an advanced control system, new sensors and analytical equipment should be installed to capture previously unmeasured variables, and a data-acquisition system should be designed to store the resulting data. Not only will a future advanced control system need this information, major benefits can be realized in many cases simply by viewing and analyzing data that was previously unavailable. With this new data, well-informed decisions can now be made, automated production reports can be designed and the facility is in position to install the next tier of projects to further optimize operations.
An implementation plan will typically begin with the installation of analytical equipment necessary to measure the key process variables. This will be followed by design of a data acquisition and historian system. Computing technology has made it possible to collect, store and mine a tremendous amount of data at low cost. The analysis of this data can result in substantial benefits, even without the installation of new control systems. Real-time process data can be used for production monitoring, optimization of gas consumption, identification of bottlenecks in the process, plant troubleshooting and improved safety using automated alarms. In addition, data acquisition and data analysis are the key enablers of advanced control and optimization of manufacturing processes.
The next phase of projects will involve installation of control hardware and programming of control strategies on individual unit operations. The final phase of projects will then link the individual controllers to optimize the entire facility.
Step 5: Measure Results
Once a productivity improvement project has been implemented, it’s important to measure the benefits realized. Monitoring and tracking the results will not only justify the reasons for undertaking the projects and determine if the overall facility goals are being met, but it will also strengthen the case for future project implementations. The data-acquisition system will allow for real-time monitoring of control-system performance and reporting of the realized benefits. Historically, advanced control-system performance tends to diminish and benefits are lost if the system is not actively supported. Therefore, continuous monitoring of performance is needed to determine whether the system is operating as designed.
Finally, it is very important to track and document any lessons learned from project implementations. This valuable information can help future projects be executed more quickly and cost effectively.
SummaryThis article proposes a five-step process resulting in a detailed plan to help optimize a heat-treating facility using automation and advanced control. The main points in this process include:
- Education and awareness on automation, sensor and advanced control technology, and how it can be applied to heat-treating processes
- Alignment between the design and implementation of advanced control projects and the overall goals and objectives of the facility
- Thorough assessment of the entire manufacturing operation
- Tiered approach to project implementation
- Measurement of results and documentation of lessons learned
For more information:Talk to one of our Applications Engineers about a complete assessment or process controls by calling us at 800-654-4567, code 474. Jake Fotopoulos is lead process controls engineer for Air Products and Chemicals, Inc.
Additional related information may be found by searching for these (and other) key words/terms via BNP Media SEARCH at www.industrialheating.com: model predictive control, furnace control system, sensors
Report Abusive Comment